Two bigger units of 1600 TR Vapor Absorption Chillers installed at CHPP in 2017.
Thai food International PCL located at Suphanburi decided to discard its age old water scrubbing system with our bag filter system. Water scrubbing was not only causing corrosion but a mess around the boiler. Water is becoming scarce and expensive moreover the required exhaust parameters were not getting maintained. E3 Asia team successfully installed bag filter on their existing boiler."
E3 Asia service team maintains their absorption chiller supplied by Thermax for process cooling as well.
โรงงาน ไทยฟูด นครปฐม ได้ตัดสินใจที่จะทิ้งระบบน้ำเสียซึ่งน้ำเสียดังกล่าวนั้นจะมีผลต่อการกัดกร่อนระบบถุงกรองของเรา ซึ่งเราเข้าใจว่าทรัพยากรน้ำนั้นเป ็นสิ่งที่หายาก และพารามิเตอร์อาจได้รับความเสียหายเมื่อถูกไอเสีย ทางเรา ทีมงาน อี3เอเชีย มีประสบการณ์ ในการติดตั้งและการบำรุงรักษา จาก เทอร์เม็ก
E3 Asia Company Limited has been appointed by Sub Anan Bio Mass Company Limited to study their plant and suggest improvisation steps to make the plant more efficient.
E 3 Asia’s team spent quality time at site to observe the fuel handling, mixing, combustion and over all thermal engineering of the plant. Currently plant is firing shredded EFB ( empty fruit bunch) with Wood chips for 8.5 MW generating power plant. Plant faces many problems like clinker formation, low efficiency and frequent stoppage of the plant. Team comprising Krishna Tiwary , Sachin Sangamnerkar, KhunTerayut collected all information which would help them stich a report for KhunDhweep, owner of SABCO.
A Final report with all calculations shall be soon submitted to SABCO management .
Kangwal polyester, second largest polyester plant in Thailand for textile grade polyester producing 260 Tons per day fiber and 50 Tons POY per day decided to choose E3 Asia company limited for it waste to energy project. For their plant located at district of Phetchaburi , about 110 km from Bangkok Thailand, E 3 Asia successfully signed a contract to supply 2 heat recovery units manufactured by Esteem power equipments , Pune India, their partnering company. .
For their polymerization plant, Kangwal utilizes 2 no,Thermax manufcatured Rice husk fired Thermic fluid heater of 6 million kcal per hour each for the indirect heating of PTA mixed with glycol . Both the heaters are in contineous operation producing waste hot gases around 28900 kg per hour at 300 degree centigrade from each heater. E 3 Asia along with its partnering company took the challenge to recover the heat to prodcue hot water which may thus be sent to their exisiitng boiler to save fuel. Extensive studies were done, site was visited by the design engineers few time and following process data were produced for each HRU;
Flue Gas Flow m3/hr 46500
Gas Inlet Temp deg c 300
Gas Outlet Temp deg c 165 (after recovery)
Effective Heat Duty kcal/hr 963283
Water Flow kg/hr 9000
Water Inlet Temp deg c 85
Temp Rise deg c 109
Water Outlet Temp deg c 194
LMTD Correcte 91.36
Area m2 253